[Nut-upsuser] Strange ups.load and battery.temperature with an APC Back-UPS RS 800 (NUT v2.2.2)
khali at linux-fr.org
Wed Jan 7 10:16:24 UTC 2009
On Tue, 06 Jan 2009 19:51:39 +0100, Arjen de Korte wrote:
> Citeren ZeusII <zeus2 at elotrolado.net>:
> > battery.temperature: 3022999999999999855
> > ups.load:
> > 460000000000000000522694688304941003169920226853844164973253026123689780561201643569637208248542908198527766044790898610404968516009252686779106462679232958642106465178573742621663105573836478844157360968769427943324469938758039552774256898399191695594881
> These problems might be related. In order to find out what is wrong,
> run the 'usbhid-ups' driver with debugging enabled (-DDDD, not higher)
> to see what is going on.
For reference, I have an APC Back-UPS RS 800 here and it says (with NUT
The load value is correct. The temperature is fake (it never changes.)
Same firmware version as in the original report (9.o4 .I).
More information about the Nut-upsuser