[Nut-upsuser] UPS restart delay
doconnor at gsoft.com.au
Fri Jul 27 08:06:35 UTC 2012
On 21/07/2012, at 22:55, Charles Lepple wrote:
>> Does anyone know if this is possible? A setting like this would provide some hysteresis for successive power failures which would be handy to have :)
> I don't know about that specific hardware, but the variables which would control this are battery.charge.restart ("Minimum battery level for UPS restart after power-off") and ups.delay.start ("Interval to wait before restarting the load (seconds)"). Check the output of "upsrw <ups>" to see if that variable is supported with your combination of UPS and driver.
> Which version of NUT are you using? There might be a newmge-shut driver included as well.
I tried mge-shut in 2.6 with no change, but newmge-shut with 2.6 showed this parameter, thanks!
Daniel O'Connor software and network engineer
for Genesis Software - http://www.gsoft.com.au
"The nice thing about standards is that there
are so many of them to choose from."
-- Andrew Tanenbaum
GPG Fingerprint - 5596 B766 97C0 0E94 4347 295E E593 DC20 7B3F CE8C
-------------- next part --------------
A non-text attachment was scrubbed...
Size: 4358 bytes
Desc: not available
More information about the Nut-upsuser