[Nut-upsuser] UPS Shutdown
roger at rogerprice.org
Thu Oct 6 02:17:55 UTC 2016
On Wed, 5 Oct 2016, Jeff Bowman wrote:
> I’m trying to better understand OffDelay and OnDelay:
> My server requires ~3½ minutes to shut itself down. Considering this I’m
> comfortable setting OffDelay to 300 (five minutes).
> How does this work in conjunction with the UPS hardware? Does NUT
> immediately send a command to the UPS to wait for 300 seconds and then
> shut itself down, thereby allowing the server enough time to safely shut
> itself down as well?
> This is the only way I can think of that the arrangement can work. As
> it’s naturally impossible for a turned-off computer to send any command
> anywhere, an option for sending a “take-this-now-but act-on-it-later”
> command surely must exist.
The command is "upsdrvctl shutdown".
> I’ll be initiating my own shutdown sequence as a result of NOTIFYCMD
> with a NOTIFYTYPE of ONBATT. My process will poll battery status for
> five minutes (to reduce false positives) before finally deciding to send
> individual shutdown commands to the server, NAS, other devices, etc. In
> other words, I’m going to write my own upssched, suited specifically to
> my platform and configuration needs.
> Given this configuration, at what point will the 300 seconds start
> counting down? What trigger sends the actual command which in turn tells
> the UPS hardware to start that countdown? The documentation is unclear
> on this finer point.
The 300 seconds start when the effect of "upsdrvctl shutdown" reaches the
UPS hardware. See the diagrams at
http://rogerprice.org/NUT.html#SYSD_RACE which assume an offdelay of 20
More information about the Nut-upsuser