[Nut-upsuser] TrippLite SU3000XLCD
clepple at gmail.com
Fri Oct 21 02:05:39 UTC 2016
[please use reply-all to include the list - the headers are not mangled]
On Oct 20, 2016, at 3:22 PM, Fairfax, Charles A. wrote:
> I’m having trouble with a TrippLite SU3000XLCD. I’m using a Raspberry Pi running Raspbian (wheezy) with NUT 2.6.4.
> I can monitor my older TrippLite UPSs, mostly SU1000RT2Us, with this Pi and a USB to serial adapter.
Interesting, we don't have that model number listed in our compatibility list[*]. Do they mostly use tripplitesu or tripplite?
> My first thought with the SU3000XLCD was to use the USB port instead of the serial port as that’s the “modern” thing to do. When I plugged the USB cable in to the UPS it turned off, dropping the load. The load is process control instrumentation which, while not damaged, presented some challenges to restart. So now I’m leery of using the USB port.
> With a long history of success monitoring UPSs via serial communication that’s where I am now. Unfortunately NUT doesn’t see the UPS.
> My query is two part:
> 1) Is there a reasonable explanation for why plugging my Pi into the UPSs USB port caused it to turn off? Is there a proper way to connect it that will avoid this? If so my problem is likely solved if the usbhid-ups driver will talk to my SU3000XLCD. If I can’t assure my employers that I won’t kill the process again USB may not be a viable option.
To be honest, I would have expected the RPi to reboot when inserting the USB cable.
Was the Pi plugged into a computer or a standalone USB adapter? I wonder if there was a difference in ground potential between the Pi and the UPS.
The entry on the HCL for the SU3000XLCD came from NUT USB testing that Tripp Lite performed in their lab: http://article.gmane.org/gmane.comp.monitoring.nut.user/8173 . For that reason, I would think it would be reasonable to bother Tripp Lite about this issue, especially if it crops up again.
> 2) Connecting to the serial port has not (yet) shut down the UPS. This is a good start but it would be better if communication happened. Should I be able to communicate via serial port with this SU3000XLCD with one of these drivers? Is there another driver that’s known to work with this UPS or can this one be “tweaked” to work? Can it be as simple as a baud rate mismatch? I’m not having much luck querying the serial port’s settings.
Although the old "tripplite_usb" driver seems to be talking to a USB-to-serial chip with a very similar protocol to the "tripplite" driver, I don't think we ever got anywhere on trying to combine the two. Also, since the SU3000XLCD is listed as compatible with the usbhid-ups driver rather than tripplite_usb, I don't know if we can draw any conclusions from the older driver.
Do you have access to a spare SU3000XLCD? We could try patching the tripplite serial driver to send a protocol query, and work from there. However, I wouldn't want to experiment on the production system.
Another thing to note: some UPSes don't like switching between the USB and serial ports after they have powered up. I don't remember if we ever confirmed if this affects Tripp Lite hardware, but it is something to be aware of.
More information about the Nut-upsuser