[Nut-upsuser] problem with nut APC BackUPS RS 1500 (white)
clepple at gmail.com
Wed Mar 28 01:21:02 UTC 2018
On Mar 27, 2018, at 5:47 PM, <p1_p1_p1 at seznam.cz> wrote:
> if somebody has same problem with APC BackUPS (SmartUPS works correctly in same USB)
> USE FASTEST USB that U have on board, (if you have USB 2.0 and USB 3.0 onboard use one 3.0 port for UPS),
> sounds like nonsense, but it works, just OMG and halelujah for linux usb drivers.
According to this, your UPS is using the slowest possible USB 1.1 signaling rate, so success after changing from a 2.0 to a 3.0 port might just be coincidence:
T: Bus=02 Lev=02 Prnt=03 Port=00 Cnt=01 Dev#= 4 Spd=1.5 MxCh= 0
D: Ver= 1.10 Cls=00(>ifc ) Sub=00 Prot=00 MxPS= 8 #Cfgs= 1
P: Vendor=051d ProdID=0002 Rev=01.06
S: Manufacturer=American Power Conversion
S: Product=Back-UPS RS 1500 FW:8.g9 .I USB FW:g9
Also, if you are having intermittent trouble with drivers, you can use the maxrestart and retrydelay options: http://networkupstools.org/docs/man/ups.conf.html
We have had some reports of issues with VMware and USB. This can affect systems with APC UPSes, because the driver needs to be able to pull the model number to apply model-specific fixes. Versions after NUT 2.7.2 have a partial fix for this, but in your case, you should be able to automatically retry with the aforementioned options.
More information about the Nut-upsuser