[Nut-upsuser] Low battery unexpected shutdown
roger at rogerprice.org
Thu Apr 23 21:04:14 BST 2020
On Thu, 23 Apr 2020, Marc Franquesa wrote:
> ...this email reports:
> Power ups UPSdevice battery-low notification
> UPS: UPSdevice at power.srv.l3jane.net
> Notice type: LOWBATT
> Message: battery-low
> Sun, 19 Apr 2020 12:10:27 +0200
> Charge 73%
> Charge Low 20%
> Runtime 15m52s
> Delay Shutdown 20s
> Delay Start 30s
> Firmware 02
> Load 21%
> Power Nominal 1200VA
> Status FSD
> ALARM OB LB
Assuming the battery is ok, then how long does it take this system to shut down?
Is a Delay Shutdown of only 20 sec enough?
> So, indeed was in LowBattery and FSD shutdown, however note that the current
> charge was 73% >> 20% low battery, so why it set LB when there were enough
> battery to run? Is this a comm problem, device issue, driver ?
System administrators sometimes use the command
upsrw -s battery.charge.low=75 -u <upsuser> -p <sekret> <myups>
to speed up NUT testing. Do you have such a command lurking somewhere?
> A) Can upsched introduce some race-conditions making a timer cancel cancel
> other timers not related ?
The upssched timers operate independently of one another. Unless you have
strange logic in upssched-cmd the heartbeat timers should not affect any other
timer. If you are shutting down on LB, then why do you need timers in upssched
(apart from the heartbeart)?
More information about the Nut-upsuser