[Nut-upsuser] HP R1500 G2 UPS
Arjen de Korte
nut+users at de-korte.org
Fri Feb 19 11:30:50 UTC 2010
Citeren Kjell Claesson <kjell.claesson op epost.tidanet.se>:
>> ups.alarm: BATTERIES_DISCONNECTED
>> ups.status: ALARM OL
> Can you confirm that you have disconnected the battery.
> So we don't have a problem parsing the alarm block.
The values reported from the UPS look suspect.
Both battery.voltage and battery.charge look really low for a UPS that
is running on mains and the ambient.temperature is a bit high. These
could be correct if the mains voltage has just returned after an
outage or a battery test was just finished. If this is not the case,
I'd say the battery is bad and needs to be replaced.
Best regards, Arjen
Please keep list traffic on the list
More information about the Nut-upsuser