[Nut-upsuser] TRIPPLITE OMNIVSINT80 Compatibility
dave at opensourcesolutions.co.uk
Fri Sep 26 22:10:41 UTC 2014
On 09:18, Fri 26 Sep 14, Charles Lepple wrote:
> The commit listed above (f61eadb5) includes the scaling, and it is on master (currently 4b753dc7). If upsc shows "driver.version.internal: 0.28" or 0.29, you have it all installed correctly.
Now looks improved (compiled from commit 4b753dc7 src):
device.mfr: Tripp Lite
ups.debug.V: 32 30 32 58 58 58 0d '202XXX.'
ups.firmware.aux: protocol 1001
ups.mfr: Tripp Lite
Measuring the real voltages shows input.voltage is reading high by 2%
and output.voltage low by 6.5% (real voltage is 243.8V and output 244.2V atm).
The measurements reported by the UPS seem to vary quite markedly
between invocations of upsc so I can only assume the A/D used has only a few
bits resolution or the sample window is small. On bypass input.voltage
should = output.voltage of course.
> > My guess its what it would expect to see so you can relate input.voltage
> > to it. In that respect its 230V for the territory the model is sold into
> > even though Tripp lite are selling it as a 240V model. Either way the
> > differentiation only has to deal with 2x0V versus 110V and so unlikely
> > to be the source of any confusion.
> In that case, I'm inclined to change it back to 230V before the next release, since we don't have any more accurate information as to what the 'V' digits really mean.
More information about the Nut-upsuser