[Nut-upsuser] empty ups.status on TrippLite SMART1500RMXL2U
justin at techadvise.com
Thu Jan 24 16:31:38 UTC 2008
On Wed, 2008-01-23 at 07:31 -0500, Charles Lepple wrote:
> ups.power.nominal seems like it should be 1500 instead of 150. Is the
> input voltage actually 120 VAC? How are the outlets grouped? (That is,
> how many are switchable, and how many are on all the time?) Also, what
> are the USB product and vendor IDs (available from lsusb)?
The Windows software also reports protocol 0004. This is an old unit,
probably 5 years old or so. I looked, but didn't see any way to update
firmware on this UPS.
It's a 1500VA, so yeah, no idea why it reads 150. Input is 120V.
There are two load groups, load 1 is switchable, and has two outlets on
it. load group 2 is not switchable, and contains the other six outlets.
I'm running Nut in an embedded environment, and don't have lsusb
available. I can setup Nut on my laptop for testing if need be, but
here's the relevant section of /proc/bus/usb/devices:
T: Bus=02 Lev=01 Prnt=01 Port=00 Cnt=01 Dev#= 4 Spd=1.5 MxCh= 0
D: Ver= 1.10 Cls=00(>ifc ) Sub=00 Prot=00 MxPS= 8 #Cfgs= 1
P: Vendor=09ae ProdID=0001 Rev= 0.01
S: Manufacturer=TRIPP LITE
S: Product= Tripp Lite SMART1500RMXL2U
C:* #Ifs= 1 Cfg#= 1 Atr=80 MxPwr= 60mA
I: If#= 0 Alt= 0 #EPs= 1 Cls=03(HID ) Sub=01 Prot=00 Driver=(none)
E: Ad=81(I) Atr=03(Int.) MxPS= 8 Ivl=200ms
> If you are mainly concerned with on-battery/on-line and low battery
> indications, just hook up the unit with a dummy load (so as not to
> crash the computer when the batteries die) and run the batteries down
> while monitoring the "ups.debug.S" line.
> Even better would be to compare values directly with what the Tripp
> Lite software returns, if you have a Windows system available. If you
> go that route, we could also look at a USB protocol dump.
My primary concern is battery status, but it would be nice to have all
the other features too. I can hijack my wife's laptop for awhile to do
the dump, but I'm unfamiliar with the internals of the PowerAlert
software. What do I need to do to get you the data you need?
More information about the Nut-upsuser