[Nut-upsuser] false low battery alarm
clepple at gmail.com
Thu Feb 28 12:58:47 UTC 2013
On Feb 28, 2013, at 4:10 AM, Vieri wrote:
> input.transfer.reason : simulated power failure or UPS test
Sounds like it was the UPS self test?
> ups.mfr.date : 01/10/06
If this is the original battery, it is certainly possible that it has built up enough internal resistance that the voltage reads normal when idle, but it dips too low during a test.
> ups.test.interval : 1209600
1209600 seconds = 14 days, so if it does it again in two weeks...
clepple at gmail
More information about the Nut-upsuser